A mechanical contractor was tasked to complete a condenser barrel cleaning on a 250 ton chiller. The chiller was having issues with the approach temperature and was operating inefficiently. Based on previous experience, the contractor chose RYDLYME to dissolve the water scale from the chiller’s condenser tubes via circulation.
Fifty gallons of RYDLYME was circulated for five hours and then inspected – due to the severity of the scale deposits, an additional fifty gallons of RYDLYME was circulated to dissolve all of the efficiency robbing barrier. After circulation and final inspection, the chiller’s condenser tubes were found to be restored to bare metal and their copper shine. The approach temperature prior to the RYDLYME cleaning were 15°F. After the RYDLYME cleaning the approach temperature were reduced to 6°F! The customer was thrilled to have the equipment operating efficiently once again, saving money on their energy usage.