Descaling a Cooling Tower System with RYDLYME
Adding RYDLYME descaler to the cooling tower basin allows the tower’s transfer pump to circulate the solution throughout the entire cooling system while in operation. This can all be accommodated during the normal operation of the cooling tower without shutdown! It is imperative when calculating a required amount of RYDLYME cooling tower descaler needed for a cooling tower system to include enough RYDLYME for the equipment load of the tower. This prevents the spread of Legionnaires’ Disease.
What does a Cooling Tower do?
- Dissolves 2.2 lbs of scale per gallon of RYDLYME
- NSF/ANSI 60 certified
- Non-hazardous, non-corrosive and safe for personnel
How to Descale a Cooling Tower System:
- Close the makeup water valve to the tower basin.
- Turn off all chemical or non-chemical water treatment, conductivity meters, and pH meters.
- It is recommended that all loose water scales, lime, mud, rust, and other foreign matter be manually removed from the tower basin prior to starting the cleaning.
- Lower the water level in the tower basin to a point where the pump can maintain circulation without cavitation and close the bleed-off valve.
- It is recommended that the fans be turned off during the cleaning.
- Determine the proper amount of RYDLYME to be added to the system. Please note that the amounts recommended in the chart are just the guidelines and that your application may require 2-4 times the chart amount, depending on the severity of the deposit build-up in your system.
- To minimize excessive foaming, you may now slowly add the required amount of RYDLYME to the tower basin.
- The bubbling and foaming you will observe is a natural reaction of the RYDLYME dissolving the water-formed mineral deposits within the system.
- Once the RYDLYME is in the tower system, allow it to circulate. Start charting your pH readings or performing calcium spot tests to measure the effectiveness of the RYDLYME solution during the cleaning (“Testing the Effectiveness” is available at our website or contact us directly for a copy). If the RYDLYME cleaning solution expends prior to the completion of the recommended circulation time, there is more scale in the system. It is recommended that you repeat steps 6-9 to complete the cleaning.
- It is recommended that the RYDLYME cleaning solution be cycled out of the system to prepare it for normal operation. At this time, strainers should also be removed, inspected, and cleaned as well.