Mineral deposits can accumulate rapidly in your tankless water heater robbing you of heating efficiency and money each month. By periodically cleaning your tankless water heater with RYDLYME Biodegradable Descaler Tankless Hot-Water Descaling Kit (RTK), you can keep it operating at peak efficiency and reduce heating and water costs, as well as extend the life of your unit!
The RTK is the fast, effective, and safe solution for maintaining your tankless water heaters. By utilizing RYDLYME, the “World’s Leading Biodegradable Descaler,” you can resolve your tankless water heater scaling issues IN LESS THAN 30 MINUTES! Watch the RTK in action here or on our YouTube Channel!
ALL-IN-ONE KIT FOR TWO CLEANINGS!
The RTK provides you with all the necessary equipment and materials, including two bottles of RYDLYME for TWO tankless water heater cleanings! Just pour RYDLYME and water into the bucket, connect the hoses to your tankless water heater, turn on the pump and circulate. It’s that simple!
WHAT IS RYDLYME?
RYDLYME Biodegradable Descaler is a scientific liquid descaler specifically designed to dissolve water scale, lime, mud, rust, and other mineral deposits. For over 75 years, RYDLYME has been trusted and successfully utilized in commercial, residential, institutional, and governmental facilities!
BIODEGRADABLE WITHOUT NEUTRALIZATION!
SAFE TO HOLD IN YOUR HAND WITHOUT INJURY!
SAFE ON METALS & MATERIALS FOUND IN WATER-OPERATED EQUIPMENT!
NSF/ANSI 60 CERTIFIED FOR USE IN POTABLE SYSTEMS!
SAFE TO DISPOSE OF DOWN NORMAL DRAINS & SEWERS!
Dissolves 2.2 lbs of scale per gallon of RYDLYME
NSF/ANSI 60 certified
Non-hazardous, non-corrosive and safe for personnel
All-in-one kit for TWO cleanings!
How to Descale a Tankless Water Heater
This procedure is specifically for units that utilize isolation valves. If your unit does not have isolation valves please call Apex Engineering Products Corporation at 800.451.6291 for additional technical assistance. Always refer to the water heater manufacturer’s cleaning procedure if applicable.
Turn off the unit, gas, and cold water supply to the tank heater.
Open the bucket and remove the contents.
Fill the circulation bucket with one gallon of water or about 1/3 full. Place underneath the water heater.
Close both hot and cold isolation valves (C and D) adjacent to the tank heater.
Make sure both service valves (A and B) are closed and remove both cold and hot water service valve caps. Be aware that residual water may drip out.
Connect one of the supplied hoses to the cold water service valve (B). Be sure the fitting washers are installed before connecting, otherwise, leaks may occur.
Connect the second of the supplied hoses to the hot water service valve (A). Be sure the fitting washers are installed before connection, otherwise, leaks may occur.
Using the supplied clamp, secure the hot water service valve (A) hose to the circulation bucket in a manner that will reduce the risk of splashing/spilling.
Connect the cold water service valve hose to the pump discharge outlet (threaded). Again, be sure the fitting washers are installed before connection. Slide the filter on to pump inlet (non-threaded) and place the pump in the bucket.
Pour (1) 32oz bottle of RYDLYME into the bucket. The second included bottle is for use with your next scheduled cleaning.
Open hot and cold service valves (A and B). Any existing water volume inside the tank will drain into the bucket.
Make sure the pump is fully submerged (dry running will damage the pump). Plug the pump into an electrical outlet, and be sure that the outlet is grounded.
Allow the pump to circulate the RYDLYME solution through the tank heater for 20-30 minutes. (Check for leaks and secure if necessary. If the water volume inside the bucket drops suddenly, then there may be a severe leak.) During this time, try our included FREE sample of RYDALL MP!
Unplug the pump. Close the cold water service valve (B), disconnect the cold water hose, and reinstall the cold water service valve cap.
Discard solution down drain, place bucket underneath heater, and re-secure hot water discharge hose.
Open cold water supply and cold isolation valves (D).
Flush the tank heater for 5 minutes or until the water is clear.
Close the cold water supply and empty the bucket as needed.
Close the hot water service valve (A), disconnect the hot water hose, and reinstall the hot water service valve cap. Open the hot water isolation valve (C).